Creating a niche of Gas Distribution Panel such as Area Alarm Panel, Automatic Changeover Panel, Control Panels, Digital Display Area Alarm Panel and Semi Automatic Control Panel at its best, with utmost quality.
Area Alarm Panel
These alarms are absolutely reliable as reputed pressure sensors and microprocessor are used. With an in-built On-Off switch, the single units can be kept off as and when necessary. The visual alarms will be active in case of slight abnormality in line pressure and audio-visual alarms will become active only in case of any major abnormality in the line pressure and can be acknowledged by pressing the MUTE button provided in the system. (See table below for Pressure & Alarm Relation.) The audio alarm will restart automatically in case the pressure does not come back to the normal range within 30 minutes, thus reminding the user that the fault is still unattended. The button switches ensures ease of use of the system. The TEST button provided in the system will check the system internally and can be operated at any point to make the self-test. A battery pack can be opted for uninterrupted power supply to the system and can give 2 hours back-up supply.
Digital Display of Line Pressure in psig (mm of Hg in case of Vacuum)
Audio Visual Alarm for High & Low (Only Low in case of Vacuum)
Single Gas to Four Gas Systems including Vacuum
Microprocessor Based System
Blinking Display for High and Low Alert
Reliable Pressure Sensor
Four Precaution Alarms before High & Low Final Alarms
Colour Coded Service Enclosure with Complete Separation of High & Low Voltage
Wall Mountable Enclosure made of Aluminium (Powder Coated)
These Automatic Changeover Panels operate on Pressure Differential and does not require any electricity to operate and the changeover is completely mechanical. The user gets and uninterrupted Gas Supply. When the primary cylinder gets empty, the panel starts drawing gas automatically from the reserved cylinder and the user gets an audio-visual alarm that which cylinder got empty, though the gas supply remains uninterrupted. The user can replace the empty cylinder with a filled cylinder at his convenience at a later time and now the newly replaced filled cylinder remains as standby.