Approx Price: Rs 33,333 /each
Minimum Order Quantity: 1 each
Multigrade Sand Filter also consist of a vertical or horizontal pressure vessel with a set of frontal pipe work and valves, media consist of different sizes and grade mixed and supported by layers of pebbles and gravels, a top distributor to distribute the incoming water uniformly throughout the cross section of the filter, and an under drain system to collect filtered water.
This filter performs at a substantially higher specific flow rate than conventional filters. The basic difference between Pressure Sand Filter (PSF) and Multigrade Sand Filter (MGF) are media used in vessel and velocity variation.
Advantages and Features
1. Efficient Turbidity and TSS Removal
2. Filter up to 20 – 30 Microns
3. FRP, CS, MSEP, SS Vessel available
4. ASME Pressure Vessel is also available
5. Two, Three and Multi layer filters
6. Low Pressure drop across the vessel
7. Air scouring available for high flow pressure vessel
8. Manual, Semi Automatic and Automatic features are provided
9. Long filter cycles between backwashing with minimum loss of pressure.
10. Pneumatic and electrical operating automatic valves
11. Two elliptical manholes
13. Automatic control and electrical cabinet.
Activated carbon (AC) is a natural material derived from bituminous coal, lignite, wood, coconut shell etc., activated by steam and other means, and each one have different adsorption properties (e.g. bituminous carbon for high chlorine reduction capacity). We also use various blends of carbon to achieve specific water quality and contaminants reduction (e.g. coconut shell carbon for "sweet taste").
Rapid Gravity Sand Filters
The rapid gravity sand filter is a type of filter commonly used in municipal water treatment facilities. Rapid sand filters use relatively coarse sand and other granular media to remove particles and impurities that have been trapped in a floc through the use of flocculation chemicals - typically salts of aluminium or iron. Water and flocs flows through the filter medium under gravity pressure and the flocculated material are trapped in the sand matrix.
Rapid filters are usually built open with the water passing down the filter but by gravity. It has a filter rate of 4 – 8 m3/m2/hr. The tank is made of concrete with a depth of 3.0 to 3.5m. Coarse sand of size 0.4 to 1.5mm is used as the filter medium.
A screen filter is a type of filter utilizing a rigid or flexible screen to separate sand and other fine particles out of water for irrigation or other applications. Typical screen materials include stainless steel (Mesh), polypropylene, and nylon.
Side stream Filters normally used for industrial cooling tower. Cooling Towers, by design, flush airborne contamination such as biocides, heat, slime or silt into the system, where they deposit on heat exchange surfaces. Suspended matter in the cooling water also supplies living microorganisms with a constant food source for sustaining life and multiplying. Max-ion provide suitable cooling tower side stream Filter (SSF) which can remove all the physical contamination from the water which affects the life and efficiency of the cooling towers system.
Advantages and Features
A] Condensed Water Piping Side Stream Sand Filter
B] Cooling Tower Basin / Pond Side Stream Filtration
(iv) Housing Flats
(v) Tea Garden
(vi) Industry etc.
50 litres/hr to 300000 litres/hr.
No Salt required – Time & Cost saving
Is attached as a part of the pipeline
Works without operator
Good for human consumption
Zero maintenance units
Magnets have a life of about 20-25 years.
Continuous flow without choking
Useful for generators in scale removal
Generate zero pollution
Removes existing scales (Calcium & Magnesium).
Output of product remain constant.
Approx Price: Rs 22,222 /each
Minimum Order Quantity: 1 each
|Water Source||River Water|
Our company is engaged in manufacturing and supplying a vast array of DM plant and Mix Bed Plant/Systems.
Mix Bed Plant is used for high purity water to used for various applications like laboratory,Industrial application,Chemical manufacturing, Glass manufacturing etc.
MAX-ION Industrial two bed demineraliser (Deionizers) Type CATION and ANION are available in a wide range range with maximum flow rate from 100 LPH to 200000 LPH.
Demineralization or Deionization is the process of removing mineral salts from water by using the ion exchange process. With most natural water sources it is possible to use Demineralization and produce water of a higher quality than conventional distillation.
Fluid Systems Manufacture a Wide range of custom-built softening, Dematerializing plants for industrial process water applications, with inherent design to conserve water, and save costs. They are available in different sizes and materials, manually operated or fully Automatic, & ready to install & are available as standard models or custom built versions for specific needs.
A Typical two-bed DM Plant consists of two FRP/MS Rubber lined Pressure vessels connected in series along with its internal fittings. The first unit consists of high capacity strongly acidic cation exchange resin, which converts positive ions of salt and replaces them with hydrogen ions to form respective acids, which are absorbed in next vessel by strongly basic anion exchange resin. The water obtained by this process shows conductivity less than 20 µ S / cm at 25o C and total dissolved solids less than 10 ppm.
Further high purity water can be achieved by Mixed Bed Deionisers, which are designed to produce high purity treated water. They can be used as polishing units after two bed DM Plant to obtain high purity water. Mixed Bed Deionisers are single column units, filled with strongly acidic cation and strongly basic anion exchange resins mixed together.
There are four distinct stages in the operation of Deionisers
In the Service cycle the water enters the vessel and passes through the Resin bed of the respective exchanger
After the resins are exhausted, the bed is backwashed. Backwashing is carried out by a uniform upward flow of water through the resin bed. The backwash step expands the resin bed releasing any entrapped particulate matter & removes the channeling in the resin column if occurred during the service cycle.
When the ion exchange resins loose all the exchangeable ions, they require regeneration to restore them back to hydrogen or hydroxyl form depending upon whether they are cation or anion resins. To achieve this 4 - 5% concentrated solution of Hydrochloric acid is used for cation resin and a 4% - 5% concentrated solution of caustic soda for anion resin. Sulphuric acid can also be used for Cation Regeneration but the concentration of acid during injection must be kept at minimum, such as to prevent calcium sulphate precipitation on the resin.
The final stage of regeneration is to rinse the resins of excess regenerant
I. Easy to install & operate
II.Complete Assembly with backwash ®eneration equipment
III.Produces DM water of high purity